40MVC / 38MVC. 40MVQ / 38MVQ. Service Manual. HighWall Duct Free Split System. Sizes To TABLE OF CONTENTS. PAGE. SAFETY. View and Download Carrier 40MVC product data online. High-Wall Duct Free Split System. 40MVC Air Conditioner pdf manual download. Also for: 38mvc. Manuals and User Guides for CARRIER 40MVC. We have 5 CARRIER 40MVC manuals available for free PDF download: Service Manual, Product Data.
|Published (Last):||24 November 2014|
|PDF File Size:||4.83 Mb|
|ePub File Size:||12.44 Mb|
|Price:||Free* [*Free Regsitration Required]|
Make sure that the drain tube slopes downward along its en- tire length. If possible, display LEDs on both the indoor and outdoor units. These compact indoor fan coil units take up very little space in the.
Compressor shall be fully hermetic rotary type. Carefully remove the mounting plate, which is attached to the back of the indoor unit.
Comments to this Manuals Your Name. Comments to this Manuals Your Name. Run interconnecting piping and wiring from outdoor unit to indoor unit.
Refrigerant Lines -in mm should be buried. Floor console ductless split system sizes 09 to 12 26 pages. Table of 40,vc Add to my manuals Add.
By pressing ‘print’ button you will print only current page.
Got it, continue to print. This manual also for: Enter text from picture: Contact your Carrier accessory condensate pump.
The red light under dif has come on and the unit will not work. Fins shall be bonded to the tubes by mechanical seasonal energy efficiency ratio of 13 at ARI conditions, and a expansion.
Run power wiring from main box to disconnect per NEC and local codes. High-wall ductless split system sizes to 40 pages. Parts List Aa Aa Fig. The fan coil is mounted on the wall, near the ceiling. Floor carroer ductless split system sizes 09 to 12 26 pages.
To print the manual completely, please, download it. Failure to follow this caution may result in equipment 4.
Carrier 40MVC Installation Instructions Manual
Got it, continue to print. Read the entire 40mc manual before starting the. Don’t show me this message again. If the installation location may be exposed to strong winduse a ends until all the connections are made. All connections between indoor and outdoor units must be as shown. Outdoor Unit Installation If the installation location may be exposed to strong winduse a ends until carrker the connections are made.
By pressing ‘print’ button you will print only current page. Run interconnecting cable through hole in wall outside to inside. Don’t show me this message again. The fan coils are attractively.
Carrier Air Conditioner 40MVC User Guide |
All minimum spacings shown in Fig. Lift indoor unit into position and route piping and drain Do not form a rise. This manual also for: Application Data If unit is exposed to strong winds it is drainage cannot be provided, unit should be equipped with recommended that a wind baffle be used. If unit is exposed to strong winds it is drainage cannot be provided, unit should be equipped with 40mv that a wind baffle be used.
High wall fan coil unit 40mc representative for drawings. Do not use thermostat wire for any connection between indoor and outdoor units. The outdoor always check the diagnostic codes displayed on the indoor unit diagnostic display is an LED on the outdoor unit board and is first. The deep vacuum method is the most positive way of assuring a system is free of air and Failure to follow this caution may result in equipment liquid water.
Conceal the tubing where possible.
CARRIER 40MVC INSTALLATION INSTRUCTIONS MANUAL Pdf Download.
The connections are sensitive to polarity. To print the manual completely, please, download it. Mount outdoor power disconnect. High-wall ductless split system sizes to 40 pages. Page 14 Catalog No: Enter text from picture: